Separate names with a comma.
so i have my greenwood 100 up and running after finding out that a line was plugged , after talking with a plummber he said i can add some...
sorry for not getting back sooner , but i just fixed the boiler on saturday , i want to thank everyone for there advise it really came in handy....
damper motor should open as soon as i plug it in, after that it should be controlled by the aqua stat i would think
i pushed on the spring mechanisim and the damper motor started to open ,as soon as i took the screwdriver out the damper would close again, i also...
yes i would be gravity feed
flow switch is on the boiler mounted on the top
yes it is
boiler isnt workimg right now . damper motor will not open . i tested it buy by passing it and the damper motor started to open
i have a temp guage on the boiler , pressure gauge after the exchanger , i have an auto fill on the other side of the heat exchanger, on the...
bolier is in the garage system has a reservor tank on the top of the boiler after the heat excanger it is a pressureized system
ok i googled it , my system is an open system ,how would air gotten into the system ,could a bad flow switch cause this
what does air bound mean ?
yes it looks simular to that WE ANDERSON FS 2 FLOW SWITCH
sorry i have no pics
i meant the flow switch
i opened the flow meter last night and pushed on the spring mecanisim with a screwdriver , the damper motor started to work . iam wondering if...
it is full to the level and it is an open system so its not pressurized till after the heat exchanger ,
i have had a greenwood boile for 4years , it had some issues to work out ,but i had it running good . this season i fired it up and noticed i...