Separate names with a comma.
You need diverter tees they are also called mono Flo tees.
Weighted flow checks are commonly used.
Gene I lost the photos I had of your system. Your wood boiler is feeding the coil in the Superstor? I can't seem to recall.
heat loss calculator
Assuming it's regular baseboard, (not cast iron) if you measure the length of all the element (emitters) and multiply by 500 that will give you a...
That needed to be said! Thank You
I concur with those suggestions, probably a quick fix once you figure out what's going on.
Unless it has no water in it..............................................
Do we know what is controlling the circulators? Does the house have hot water?
No photo's here either http://forum.heatinghelp.com/discussion/152009/burner-issues-wont-re-fire#latest
What model # aquastat and LWCO and how...
What controls the Taco? Do you have the I/O manual for the Greenwood?
How about some photos of what you have going on, then it won't be such a stab in the dark. Like of the controls and such with the covers off.
I'm guessing a bad motor on the burner. With power at B1 on the aquastat the burner should be running.
The first two models will fit a 30" by 30" footprint.
Update, it appears we've found a fix that Mr. McKraut can live with.
Just wanted to let everyone know what a great resource this forum is for all...
I think I have Office on one of my pc's, I'll sure try.
We'll get this sorted out Bob, I'll digest your last post and we'll come up with a plan.
Pt. Jeff isn't far, less than ten miles, I'm in Ridge....
Do we currently have any wires between the actuator and the Aquasmart?
The RIB will stay constantly lit when powered correctly. What I'm trying to do is get the RIB to close T-T on the Aquasmart when the 3 way valve...
Are we sure we didn't move any wires from their original position? RIB relay gets wired in parallel with the actuator.
Try wiring the RIB at the three way valve on the two terminals that have 24 volts when the three way is positioned for flow at the oil boiler.
Is the Tekmar still moving the 3 way valve?
Let us know what happens.
Get one of these http://www.functionaldevices.com/building-automation/display.php?model=RIBU1C
Take the wht/blu wire to one of the stage 2...
Where is the boiler supply sensor from the Tekmar located in the photos? It looks like it's on the supply from the Buderus.
I think I can say...
Do you have any photos? I ran into a Northeast Radiant Technology job today.
You could eliminate the 3 way valve and pipe the oil boiler primary-secondary and use the Aquasmart to power the circulator on that loop.
The Tekmar controls are pretty powerful with regard to the number of things they're able to do. System wise it seems like your "right there" just...
The real question here is why does the Tekmar go to stage two so quickly. If I didn't know any better I'd say it should stay at stage one unless...