Post in 'The Boiler Room - Wood Boilers and Furnaces' started by tjvt, May 29, 2014.
Aside from pex being a whole lot cheaper, any other advantages to pex vs. copper?
Helpful Sponsor Ads!
We'll if you don't care how it looks at all, it's a lot easier to get it where you need it. Keep in mind the fittings are much more expensive, & unless you are borrowing the tool that will be pricey too!
How about any overheat situation?
Pex surely will not handle the same heat and pressure of copper or iron pipe.
Pex expands a LOT more than copper or black iron. Just keep it in mind, not necessarily a good or bad thing.
I don't think I've read of any copper failures. I have read of pex failures.
If frozen copper will bust open. Pex usually doesn't.
I ran copper, 220 ft of 1 1/4" It stays nice where you put it, without the movement of pex. If I have to, I can sweat a fitting without running out to rent a pex tool. Copper is a one time investment.
Have people here used an equivalent amout of pex? That's a big investment in copper. As an aside, I just did my first pex plumbing job in the house, and it's very easy to do the joints.
Yes, true. But in an indoor boiler situation, I think I would be hesitant to use pex. A sudden burst of 200+° water could do some serious damage if someone was in range. Boilers can easily go over 220° in an overheat situation. I would stick with copper or black iron.
All my boilers have 1 1/4" pex in the long runs, once i got to the last 12 ft before the boiler i switch to black iron pipe. I just have a couple 90's before or after the pex joint to take up expansion. I have not notice any expansion in my systems and have not had any burst or broken pipes. Before crimp rings were so handy to get for this size i used double hose clamps on every joint with barb fitting. They are still working. So get a good pex pipe and go for it. Foamit UP
With the cost of my install going to 15 thou. + [Garn, building, plumbing] I didn't feel the need to cheap out on pipe. Copper is forever, [my opinion] plastic, well, who knows? Has it been tested for 50 years? When I was a 'new guy' at CL&P. someone made the decision to go with rubber ties to hold the wire on insulators, 10 years and thousands of rubber ties later, the sunlight broke them down, wire fell off the glass, burned down, tore bushings out of transformers, etc. They saved some money when they bought those rubber ties though.
Ya - there is also a difference between near-boiler piping, and, well, not near-boiler. Maybe the OP could clarify some on what he's planning & his boiler setup - including overheat/heat dump setup. I don't think I would want PEX on the part of my system that is going to be dumping heat if needed - or near boiler.
I agree with what everyone has said here...for most boiler installs copper would be the better (albeit more expensive) pipe choice. With many other piping applications; however, plastic pipe is likely going to prove superior over time. It really hasn't been around long enough to confirm this, but in place of what most steel/cast iron pipe has been used for, plastics (HDPE, PEX, PVC, etc.) will most likely last much longer and at a fraction of the cost. Unfortunately most plastics show a significant strength reduction around 180-200 deg F, which is a shame. Hopefully better high temp plastics will be developed soon.
I got 2 legitimate estimates for boiler install. The plumber that quoted copper was significantly cheaper than the plumber who quoted pex. This was surprising to me, but struck me as a no-brainer...go with the guy who is going to use copper and do it for less money. Not being a plumber, I wanted to make sure I wasn't overlooking something. Still sounds like a no-brainer given the circumstances.
The special tool for crimping pex rings is only 60$. Just buy it and you don't have to worry about this fear of having to go out and rent one.
I wouldn't use the PEX near the boiler for heat and expansion reasons but everywhere else it is great stuff. It has been in use for decades around the world. New tech is always slow to catch on but have you seen a plumber's truck lately? Not much copper anymore.
I love the look of copper, and it is 100% (if sweat and not pro-press) oxygen or any gas for that matter tight. PEX still allows oxygen to pass through it and the higher the temp the more oxygen. A radiant floor is a good application for PEX or any buried in concrete situation.
PEX also as mentioned will not take long term high heat of a solid-fueled appliance for the long run, look it up on here it had failed in a power outage or a circulator failure (we all can have that happen). Copper has been tested and had been installed since the 1940s and is still in service in heating systems from that era.
Copper or iron pipe all day long for near boiler piping. JMP, I almost always use copper for everything on the distribution , from boiler to zone valves or manifolds.
We always run copper or iron from the boiler to the main manifold area at the very least. The manifold itself where you will split off your zones should also be hard pipe. use Pex for your runouts to heat emitters if you want. It can be handy and there is nothing wrong with it when used in the right place or application.
I imagine that retrofitting pex might be easier.
Separate names with a comma.