OK, light with two switches stopped working. New house, so chances are it was done right in the first place. Both light switches have similar layout - black, while and red wires (and ground).... Ok, so first I am trying to identify which is the first one in line. One box has only one wire (with the 3/1) coming into it, so I assume that is NOT the first one. The other box has three wires coming into it, as well as two wire nuts.....so I assume this is the "hot" box. The wire nuts are on blacks and whites, neither of which go to the switch in that box. But they are hot - 110 volts. The switch itself is not hot! The second switch has 13 volts across black and while, which seems weird. Any guesses? Could the problem be somewhere else but inside the two boxes? I checked the light bulbs (3) in the light, and they certainly look fine.