I am building my own log splitter from used parts. My detent valve is a Energy G-100. It is about 25 years old therefore Energy no longer has any info for me. My issue is this, I don't know how to put the detent part of the valve back together. It has one ball bearing about 3/8" and 4 about 3/16" with a stout spring inside a threaded stud. On the out side of the treaded stud is another spring. Around all of this is two sleaves. One has two recessed areas for the 1/4" ball bearings. One is shallower than the other. The threaded stud screws into the sliding valve that passes through the valve body on the opposite end from the handle. I am not sure how the bigger ball bearing fits into the picture. All of this goes inside the end cap that is screwed to the end of the valve assembly. I have put it together and it won't go in reverse (over and over and over....) If anyone has had one of these torn down and know what I am talking about, I could use some help. Thank you.